God I hope not.
What’s to prevent a Fukushima in the United States? If it starts to melt down is there any way to stop it? Dou you suppose the politicians even care?
Another atomophobe thread.
It just wouldn’t be FR be without atomophobe threads.
Salem - New Jersey
"Salem Unit 1 was operating at 100% reactor power when a loss of 4 condenser circulators required a manual reactor trip in accordance with station procedures. The cause of the 4 circulators being removed from service was due to a combination of high river level and detritus from Hurricane Sandy's transit. "All control rods inserted. A subsequent loss of the 2 remaining circulators required transition of decay heat removal from condenser steam dumps to the 11-14 MS10s (atmospheric steam dump).
NINE MILE POINT - New York
"On October 29, 2012 at 2100 EDT, Nine Mile Point Unit 2 experienced an automatic initiation of the Division 1 Emergency Diesel Generator due to a loss of line 5. Line 5 is one of the 115KV offsite power sources. Line 5 was lost due to a lightening arrestor falling onto electrical components in the Scriba switchyard during high winds. "During the electrical transient, Nine Mile Point Unit 2 also experienced a feedwater level control lockup, requiring manual control. No Emergency Core Cooling Systems actuated and feedwater level control was returned to automatic. Nine Mile Point Unit 2 remained at 100% power during the loss of line 5.
PEACH BOTTOM - Pennsylvania
"Peach Bottom Atomic Power Station Control Room was notified of a loss of greater than 25% of sirens after severe storms in the area associated with Hurricane Sandy. Thirty-one (31) of 97 Emergency Planning Zone (EPZ) sirens are currently unavailable in Lancaster, York, Cecil and Harford Counties. Actions are currently being taken to restore unavailable sirens."
INDIAN POINT - New York
"On October 29, 2012, at 2241EDT, the Reactor Protection System automatically actuated at 100% reactor power due to a direct electrical trip to the Unit 3 Main Turbine Generator. The generator trip resulted in a turbine/reactor trip. All control rods fully inserted on the reactor trip. All plant equipment responded normally to the unit trip. This is reportable under 10 CFR 50.72(b)(2)(iv)(B). The plant is stable in Mode 3 at this time.
NINE MILE POINT - New York
On October 29, 2012 at 2100 EDT, Nine Mile Point Unit 1 experienced an automatic reactor scram due to a generator load reject. The cause of the load reject is currently under investigation. All control rods fully inserted and all plant systems responded per design following the scram.
OYSTER CREEK - New Jersey
At 1855 EDT on 10/29/2012, the licensee declared a Notice of Unusual Event (NOUE) per criteria HU4 for high water level in the station intake structure of greater than 4.5 feet. At the time of the notification, water level in the intake structure was approximate 4.8 feet and slowly rising. The cause of the increased water level was due to storm surge associated with Hurricane Sandy. No other station impacts were reported at the time. The licensee continues to monitor the intake levels and ocean tides.
And that is just what they are telling us about.